Aluminum wiring is a controversial subject in the real estate world. I often have clients ask questions like, “Is aluminum wiring safe?” or “Does it need to be replaced?”. My short answer is yes it is safe, and no it does not need to be replaced. However, I need to elaborate on those answers, as aluminum wiring requires special considerations.
I often hear people say that aluminum wiring has been outlawed for use in residential construction. This is not true. It is still very much allowed when installed properly.
Traditionally, copper has been (and still is) the preferred conductor since electricity’s inception in the late 1800's. It wasn’t until the 1960's, at the height of the Vietnam War era, that aluminum wiring began to be used in American homes. Copper prices were sky high as it was being used to make munitions and other products for military use. Home builders had to find an affordable alternative. That alternative was aluminum.
Copper is Better
It is well known that copper is a better electrical conductor than aluminum. The manufacturers and rating agencies knew this and required aluminum wire be sized one gauge larger than copper wire to carry the same current. Where a branch circuit to a light fixture is traditionally ran with 14 gauge copper, it would have to be ran with 12 gauge aluminum. The smaller the the gauge, the larger the wire.
Problems began to arise a short time after aluminum wire became widely used. Issues included lights flickering, cover plates on switches and receptacles would be warm to the touch, and burnt wire insulation. These were all caused by the aluminum wire overheating for several reasons we will look at below.
Aluminum wire is softer that copper which made it much more susceptible to cuts and nicks when removing insulation to make connections. When an area of a wire is damaged, that place becomes a hot spot that will overheat.
When electricity passes through a wire, it heats up. When metal heats up, it expands, and, consequently. it contracts when it cools down. Aluminum has a higher expansion rate than copper. The expansion and contraction cycle due to heating and cooling would cause what is referred to as “creep.” When connected to outlets not approved for use with aluminum wire, the wire would literally creep out from under the terminal screw holding the wire down. This created a loose connection that would overheat.
As with any metal, aluminum will oxidize, more commonly known as rusting. The difference between copper and aluminum is that the rust formed on copper is still a good electrical conductor. The rust that forms on aluminum does not conduct electricity well at all. It creates resistance that will cause overheating.
The problems noted above all occurred at the connection points like those receptacles, switches, light fixtures and at the main panel. The way to prevent these issues was, and still is, to use special connectors approved for use with both copper and aluminum. There were receptacles, switches, wire nuts, breakers and other electrical devices designed for this purpose. They should be marked or labeled with one of three markings: CO/ALR, AL-CU, or CU-AL.
Building inspectors were not common at the time when aluminum wiring was being installed. As a result, aluminum wiring was installed in many homes without connectors approved for use with aluminum. This is where the problems occurred and are still occurring today.
Stay tuned for my next post in which I will discuss more issues associated with aluminum wiring, insurance companies, and what to do if your house has aluminum wiring.
You've just built the home of your dreams. You agonized for months over design options and finishes. You stopped by countless times to see the progress. The process you thought would never end is finally complete and you're wondering if you should have it privately inspected. The answer is a resounding yes!
A common misconception many people have is that newly constructed homes don't need to be inspected. This couldn't be further from the truth. You are making a lifetime investment in your new home and you need to be sure it is built to last a lifetime as well. I've encountered way too many problems when inspecting new construction homes to believe that there is such thing as a perfectly built home that doesn't need to be inspected.
One myth some builders will tell you is the home has been inspected and passed multiple times by the municipal inspector as part of the permit process, therefore a private inspection would be a waste of your money. Understand that municipal inspectors are often overworked to the point that they don't have time to thoroughly inspect every single aspect of your home. I am in no way saying municipal inspectors are not good at their jobs, they just simply don't have the time. They do a great job of ensuring that homes are built in accordance with current building codes. Keep in mind, however, that building codes are the minimum standards to which the home must conform to. There is a huge gray area between building codes, quality workmanship and best practices. Any reputable builder should welcome a private home inspection. Even the best builders can and do miss things during the construction process.
Another myth regarding new construction inspections is since it is brand new, there can't be any problems. While new homes don't have the same problems as existing homes (such as aging building components nearing the end of their lifespan), they come with their own set of problems, usually related to improper construction techniques. While the average homeowner may notice cosmetic issues, without the knowledge of building codes and proper construction methods or best practices, they may overlook more serious problems. Private home inspections are by no means a code compliance inspection, however, licensed new construction home inspectors understand current building code requirements and construction methods in order to be able to identify any major issues.
Below are a few photos of issues I have found during new construction inspections.
This roof had a large hole in it where conduit for planned overhead power supply had been removed.
This house had a broken window in the attic.
I often find loose wires that were forgotten.
Hopefully these pictures help reinforce my point; new construction homes need to be inspected too!
Colin is a Certified Professional Home Inspector as well as a licensed MS Residential Builder. He has been remodeling homes since he was 14 and even built his own house by hand from the ground up. Colin is also the owner of Wilson Home Inspections.